GENERIC 16BW-1/2 DRIVER DOWNLOAD
Smoke and draft control doors complying with UL shall be labeled in accordance with Section Corner protection is not required on concrete columns in open or enclosed parking garages. Openings are not permitted in party walls constructed in accordance with Section Fire partitions shall have a fire-resistance rating of not less than 1 hour. If noncontinuous, such elements shall have closed ends, with not less than 4 inches mm of separation between sections.
|Date Added:||10 December 2018|
|File Size:||54.59 Mb|
|Operating Systems:||Windows NT/2000/XP/2003/2003/7/8/10 MacOS 10/X|
|Price:||Free* [*Free Regsitration Required]|
Ducts and air transfer openings of fire barriers shall be protected with approved fire dampers installed in accordance with their listing. Noncombustible penetrating items shall not connect to combustible materials beyond the point of firestopping unless it can be demonstrated that the fire-resistance integrity of the horizontal assembly is maintained. Combustible piping within partitions or shaft enclosures installed in accordance with the provisions of this code.
Where a certificate of inspection is furnished by an approved testing agency, the certificate shall state that the door conforms to the requirements of design, materials and construction, but has not been subjected to the fire test.
Smoke barriers used for areas of refuge in accordance with Section Corridor dampers shall demonstrate acceptable closure performance when subjected to feet per minute 0. The fire barriers or horizontal assembliesor both, separating a single occupancy into genrric fire areas shall have a fire-resistance rating of not less than that indicated in Table The lower roof assembly within 4 feet mm of the wall has not less than a 1-hour fire-resistance rating and the entire length and span generi supporting elements for the rated roof assembly has a fire-resistance rating of not less than 1 hour.
Download Generic 16BW-1/2 Scanner Computer Driver Update
Where the horizontal assembly separates mixed occupancies, the assembly shall have a fire-resistance rating of not less than that required by Section Where a smoke damper is installed within a duct, a smoke detector shall be installed inside the duct or outside the duct with sampling tubes protruding into the duct. Doors installed across a corridor. Doors installed in the elevator lobby walls of underground buildings in genefic with Section If noncontinuous, such elements shall have closed ends, with at least 4 inches mm of separation between sections.
Fire walls shall extend to the outer edge of horizontal projecting elements such as balconies, roof overhangs, canopies, marquees and similar projections that are within 4 feet mm of the fire wall. By solid fireblocking in accordance with Section Floor fire door assemblies shall be labeled by an approved agency. Automatic-closing fire door assemblies shall be self-closing in accordance with NFPA Fire walls shall have a fire-resistance rating of not less than that required by Table Vertical openings for floor fire doors and access doors shall be permitted where protected by Section Combustible projections extending to within 5 feet mm of the line used to determine the fire separation distance shall be of not less than 1-hour fire-resistance-rated construction, Type IV construction, fire-retardant-treated wood or as required by Section Exterior walls shall be fire-resistance-rated in accordance with Tables and and this section.
Fire barriers shall be of materials permitted gejeric the building teneric of construction. Horizontal sliding doors in smoke barriers that comply with Sections Batts or blankets of mineral wool or mineral fiber.
Access doors in ducts shall be tight fitting and suitable for generif required duct construction. Grease ducts shall be protected in accordance with the mechanical code.
Fire barriers installed as required elsewhere in this code or the Florida Fire Prevention Code shall comply with this section. Fire-protection-rated glazing in fire window assemblies shall be tested in accordance with and shall meet the acceptance criteria of NFPA or UL 9.
Interior exit stairways and interior exit ramps shall be protected in accordance with the requirements of Section Smoke partitions shall extend from the top of the foundation or floor below to the underside of the floor or roof sheathing, deck or slab above or to the underside of the ceiling above where the ceiling membrane is constructed to limit the transfer of smoke.
A shaft enclosure containing a refuse chute or laundry chute shall not be used for any other purpose and shall terminate in a room protected in accordance with Section The access openings shall not reduce the fire-resistance rating of the assembly. Damper actuation shall be in accordance with Sections Openings in a shaft enclosure shall be protected in accordance with Section as required for fire barriers.
Generic 16BW-1/2 TWAIN Device driver free download for windows – VMware, – VMware Virtual Platform
Pipes, wires, conduits, ducts or other service facilities shall not be embedded in the required fire protective covering of a structural member that is required to be individually encased. Ceiling radiation dampers shall be installed in accordance with the details listed in the fire-resistance-rated assembly and the manufacturer’s instructions and the listing. Where exterior walls serve as a part of a required fire-resistance-rated separation, such walls shall comply with the 16wb-1/2 of Section for exterior wallsand the fire-resistance-rated separation requirements shall not apply.